Additional specifications and description
Is there sufficient fresh air supply?
This indoor air quality sensor measures temperature, relative humidity, air quality (TVOC) and ambient light level. It has a built-in buzzer. when the TVOC level enters the alert zone, the buzzer is activated to indicate that extra fresh air supply is required. The LED indicators offer a clear, visual indication of the TVOC level via the green, yellow and red LED. The green LED indicates that the TVOC level is within range - there is sufficient fresh air supply. When the TVOC level enters the alert range, the yellow LED lights up. Red means: TVOC out of range or insufficient fresh air supply. The measured temperature, relative humidity, TVOC, dew point and ambient light level are available via Modbus RTU.
How to control fresh air supply?
The output of this sensor can control an EC fan, an AC fan speed controller or a damper actuator. The output value varies proportionally in function of the measured temperature, humidity and TVOC concentration. When more fresh air is required, the sensor will increase the fan speed or open the damper to keep all values in the predefined ranges.
Easy to connect!
The cage clamp terminal blocks reduce wiring and installation time. They eliminate the need for routine maintenance and guarantee a reliable contact for solid or stranded wires. The supply voltage is 24 VDC. The ground terminals of the power supply (V-) and output (GND) are internally not connected. This means that a 4-wire cable is required to connect this sensor. Most 24 VDC power supplies offer protection against short circuit, overload and overvoltage. A 24 VDC supply voltage increases the safety and reliability of your installation.
Flush mounting or surface mounting
The enclosure offers an IP30 protection against ingress of dust and moisture. It allows surface or inset mounting. To ensure optimal performance, it should be protected from direct sunlight. This sensor can be mounted on a wall, a flat surface or in a standard European wall mounting box. Only the front plate of the sensor is then visible on the wall - the sensor is flush mounted.
This sensor doesn't require any configuration. Once installed, it is ready to use. The default settings will do for most applications. If necessary, the settings can be adjusted via Modbus RTU communication. For example, a different output type can be selected to make it compatible with other devices: 0-10 VDC / 0-20 mA / 0-100 % PWM / Modbus RTU. Also the light intensity of the LEDs for status indication is adjustable. The Modbus register map provides a complete overview of all adjustable settings.
The best quality and reliability
This HVAC sensor is manufactured in Europe. Each sensor is calibrated and tested in our factory. In the unlikely event of TVOC sensor element failure, this module can be replaced. We use sensor elements and components of high quality. This ensures the long-term stability and accuracy of this HVAC transmitter.