Sentera devices can be connected together via ‘PoM’ or ‘Power over Modbus’. This means that both Modbus RTU communication and 24 VDC power supply are distributed via one Unshielded Twisted Pair (UTP) network cable.
Larger networks containing many devices, should be split into different segments. For each segment, the total current consumption must remain limited to 1,5 A maximum.
To select the correct power supply, calculate the total sum of the maximum current consumption of all connected devices in the segment. Select a power supply with sufficient capacity to provide power supply to all connected devices, based on this sum. We advise to use not more than 90 % (*) of the maximum capacity of the power supply to compensate power losses in the cables and inrush currents during start up.
(*) Depending on the products connected to the PoM network.
Indoor Air Quality in hospitalsWhy is air quality in hospitals so important? A hospital is a place where both weak and healthy people come into close contact with each other. In Corona times, that is a frightening scenario that requires many precautions to make this possible in safe conditions. Monitoring indoor air quality is one of these precautions.>>>
Sentera provides innovative, easy-to-use control solutions for HVAC installations and ventilation systems. How to optimise your comfort, indoor air quality, safety and overall wellbeing? We have the answer!