parameters of Sentera devices can be read and adjusted via Modbus RTU
communication. These parameters can be subdivided into Input registers and
Holding registers. Input registers are read-only. They contain information
that can be read, but they cannot be modified. The values of the Holding
registerscan be changed. Settings that determine the functionality of
the device are usually contained in Holding registers. For a complete overview
of all parameters, consult the Modbus register map of the device.
facilitate configuration and monitoring of your Sentera device, we advise to
use one of following options:
software This software allows you to monitor or configure
Sentera devices. Install the 3SModbus software and connect
your Sentera device(s) to the computer. We advise to use the CNVT-USB-RS485-V2
converter to connect your Sentera device(s) to the computer. The connected
devices are automatically detected. By clicking on them, you can monitor or
change the parameter settings.
configurator If you do not want to use a computer to
configure your Sentera device, SENSISTANT is
the best option. SENSISTANT is a Modbus configurator. Connect SENSISTANT to a
Sentera HVAC sensor or fan speed controller and adjust the
CO2 sensors with visual and audible alertToo high CO2 concentrations? Sentera CO2 sensors are now available with audible alert. On top of that, the green, yellow and red LED offer a clear, visual indication of the CO2 level. The supply voltage is 230 V or 24 V.>>>
Sentera provides innovative, easy-to-use control solutions for HVAC installations and ventilation systems. How to optimise your comfort, indoor air quality, safety and overall wellbeing? We have the answer!