Can I control multiple motors with one fan speed controller?
Motor and fan related questions
Yes, that is possible.
If doing so, make sure that:
- All connected motors are identical.
- The fan speed controller is selected, based on the total motor current required, by adding together the rated current of all the connected motors. The selected fan speed controller must have a maximum current rating that is equal or higher than this sum.
- Each motor is protected by an individual thermal overload.
- The motors remain permanently connected to the fan speed controller and are not individually started or stopped whilst the fan speed controller is enabled.
- When using a frequency inverter: operate in V/F Mode only and apply an output filter.
In the scenario of one fan speed controller per motor, each motor can be controlled separately and run at a different speed. This is not the case when multiple motors are controlled via one fan speed controller. Secondly, running multiple motors from one fan speed controller creates a single point of failure.
Indoor Air Quality in hospitalsWhy is air quality in hospitals so important? A hospital is a place where both weak and healthy people come into close contact with each other. In Corona times, that is a frightening scenario that requires many precautions to make this possible in safe conditions. Monitoring indoor air quality is one of these precautions.>>>
Sentera provides innovative, easy-to-use control solutions for HVAC installations and ventilation systems. How to optimise your comfort, indoor air quality, safety and overall wellbeing? We have the answer!