Kick start versus Soft start - what is the difference?
Motor and fan related questions
Kick start and soft start are two differentways to start up a motor or fan. The best acceleration method depends on your application. Applications with high inertia might need a higher torque at start up to avoid stalling of the motor.
Kick start — the motor will accelerate immediately from standstill towards maximum speed. The full motor torque is almost immediately available. After this start-up period (typically 8 – 10 s), the motor will decelerate towards the requested fan speed setpoint. This starting method is often used to avoid motor stalling at low speed. The disadvantage is the mechanical stress at start-up and a high motor start current.
Soft start — the motor will smoothly accelerate from standstill towards the requested fan speed setpoint. This starting method gives you the advantage of reduced mechanical stress and lower motor starting currents. Due to the reduced motor torque during start up, this acceleration method is not ideal for high inertia applications.
Merry Christmas & Happy New Year!2020 was a special year. May the present year still end on a cheerful note and make way for a serene New Year, safe and rich in freedom and healthiness.>>>
Sentera provides innovative, easy-to-use control solutions for HVAC installations and ventilation systems. How to optimise your comfort, indoor air quality, safety and overall wellbeing? We have the answer!